DetailsThe S365 Charging Jacket Is A Reliable Way To Charge TXV Systems In Cold Weather. Normally, Low Temperatures Remove Too Much Heat From The Condenser Coils, So Hvacr Professionals Should Only Work On TXV Systems When The Outside Air Temperature Is 70 °F or Higher.Now, The New Fieldpiece Charging Jacket Solves That Problem, and TXV Systems Can Be Accurately Charged Down To 37 °F Outside Temps. It's The Perfect Tool To Dramatically Extend The Hours In A Day, and The Days In A Year, Where Techs Can Install, Service, and Charge TXV Systems.Made From Parachute-Grade Material, The Charging Jacket Is Attached To The Top Of A Split TXV System with Hooks, So That The Air Inlet Is Not Restricted. Then The Unit Is Turned On The The Jacket Puffs Up From The Air Being Forced Out Of The Air Outlet.The Top Is Then Adjusted with A Drawstring Until The Proper Pressure Differential Is Reached Between The High and Low Side (Between 160 PSI and 220 PSI For R410A; and Between 100 PSI and 145 PSI For R22). Once The Systems Stabilizes For 15 Minutes At The Correct Pressure Differential, The System Is Ready To Be Charged.
- Charge TXV Systems From 37 °F -70 °F Outside
- Service Maintenance Contracts Before and After The Summer Heat
- Easy To Adjust To Reach Correct Pressure Differential
- Great Way To Increase Business During The Slow Season
- Field Tested For Accuracy
HVAC/R Professionals Can Now Dramatically Extend Their Billable Hours Because They Can Work On Systems During The Off Season. So Instead Of Having The Do Service Contract Check-Ups During The Summer Rush, Service and Maintenance Can Be Start Early In The Spring, and Continue Late Into The Fall. and Even Year-Round In Many Parts Of The Country.
California residents: see Proposition 65 Warning
Weight 2 Pounds (Lb) Width 7.5 Inches (In) Height 4.5 Inches (In) Country of Origin TWN Length 17.5 Inches (In) Brand Fieldpiece® Auto Power Off No Display No Includes Case No Features Use to charge TXV systems in cold weather - Works in outside temperatures between 37°F and 70°F - Easily attaches to the condensing unit with hooks and draw string - Simply adjust until proper difference between high and low side pressures is reached Type Specialty Test Instruments